Convoluted 316L Stainless Steel Braided Hose
Convoluted 316L Stainless Steel Braided Hose is constructed of stainless steel for minimal permeation or absorption. The convoluted core allows for flexibility, and limits kinking. Available with a wide variety of end connections. Suitable for high-temperature, vacuum, medium-pressure, corrosive or general-purpose environments.
FX Series—High-Pressure Metal Hose
|Materials||Core: 316L annular convoluted SS|
|Reinforcement: 321 SS double braid|
|End connections: 316 SS|
|Nominal Hose Sizes||Nominal Hose Sizes 1/4, 3/8, 1/2, 3/4, 1, 1 1/4, 1 1/2, and 2 in.
|Working Pressures||Vacuum to 6000 psig (413 bar) for 1/4 in.
Vacuum to 5000 psig (344 bar) for 3/8 in.
Vacuum to 4500 psig (310 bar) for 1/2 in.
Vacuum to 3600 psig (248 bar) for 3/4 in.
Vacuum to 3000 psig (206 bar) for 1 in.
Vacuum to 2600 psig (179 bar) for 1 1/4 in.
Vacuum to 2200 psig (151 bar) for 1 1/2 in.
Vacuum to 1675 psig (115 bar) for 2 in.
|Temperature Range||-325 to 1000°F (-200 to 537°C)|
|End Connections||Swagelok tube fittings, Swagelok tube adapters, NPT fittings, VCR® metal gasket face seal fittings, female VCO® O-ring face seal fittings, SAE 37° (JIC) female swivel fittings, tube butt welds
FM, FJ, and FL Series—Metal Hose
|Materials||Core: convoluted 316L SS|
||Reinforcement: SS braid|
||End connections: 316 SS|
|Nominal Hose Sizes||1/4 through 2 in.|
|Working Pressures||Vacuum to 3100 psig (213 bar)|
|Temperature Range||-325 to 850°F (–200 to 454°C)|
|End Connections|| Swagelok tube fittings, Swagelok tube adapters, NPT fittings, VCR® metal gasket face seal fittings, female VCO® O-ring face seal fittings, SAE 37° (JIC) female swivel fittings, tube butt welds
View and purchase our most widely used products.
"Safe Product Selection:
The complete catalog contents must be reviewed to ensure that the system designer and user make a safe product selection. When selecting products, the total system design must be considered to ensure safe, trouble-free performance. Function, material compatibility, adequate ratings, proper installation, operation, and maintenance are the responsibilities of the system designer and user.